Paul, shut off the circuit breaker that serves the ejector pump, and then check the float switch in the sump. The float switch may be stuck in the on position. Some ejector pumps are controlled by a pressure switch. If your pump has a pressure switch, then the pump must be removed and the switch must be replaced. Typically float switches do not fail in the “closed” position.