Select Page

# Hoyt Gas Hot Water Heater

Home Forums Public Forums Gas & Gasfitting Hoyt Gas Hot Water Heater

• Author
Posts
• #278139
afward

Installed Hoyt 40HM-EV water heater. The documentation states 34000 BTU is required to heat 28.6 gallons per hour at a 100 degree F.
rise. My calculations indicate 17000 BTU needed. However, my data is not factored by an efficiency rating. Therefore, I must assume the Hoyt heater efficiency is 50%. Can some tell me what efficiencies are normal for gas hot water heaters.

• #297825
Guest
Participant

Did you calculate at 70, 80, and 90F rises in temperature? The incoming water is colder in the winter and warmer in the summer, so the rise changes. Your calculation would be for warmer ground water temperatures. An average betweeon 70 and 90 would be 80.

40 8.33 80 = 26,656 btu.
26,656 divided by 34,000 = .78 which is about where many water heaters are near – about 80% efficiency.

• #297826
Guest
Participant

The example above is just the combustion efficiency. Taking your 28.6 8.33 100, you get 23,824 btu … divided by 34,000 = .7

70% may be the expected total efficiency after losses from the jacket and up the flue. This is the final efficiency.

• #297827
fourth year
Participant

Just as an aside, where did you find a Hoyt water heater? They have been out of business for 15 years or so, unless they started up again.