- This topic has 2 replies, 3 voices, and was last updated 22 years ago by bungie.
18 Nov 2001 at 10:27 pm #275374MasterPlumbersKeymaster
I am in dire need of a plumber who understands storm water drains. I have had news gutters and
drains installed (at great expense..for me) but there has not been enough provision made for the amount of water going down. Recent storms last week and on the weekend were disastrous. I need the opinion from someone who can HELP ME SOLVE THE PROBLEM. I have read a couple of letters to you and it seems you do have people who are aware of the physics of water flowing through pipes. I thought the last plumber knew what he was doing, but obviously not. I phoned him immediately after the first storm, but he “can’t come” to even talk about the problem for two weeks!!!
After all the money I have paid for digging up the
backyard and installation, you would think that he would have a little more professional concern. My
constant question had been when he was digging it all up and laying down new pipes: Is that pipe going to be wide enough for all of the water coming down in the new gutters? I had had a new roof put on and garge built in. the first rains after that had flooded out the garge as the roof people had put it on the gutters wrongly. three tries latter, it is strill not right..
Anyway, the plumber assured me, yes.
That was the widest pipe you could get and it would do the job. Can you please. please recommend someone to me WHO KNOWS ABLOUT THE RATIO OF WATER FLOWING DOWNWARDS, SIDEWAYS, ETC, WHEN THERE IS MAXIMUM DOWNPOUR FROM A STORM IN BRISBANE. I am in desperate need of good advise from someone who can work things out. I have abridged the story of my woes soemwhat here and have had so many things go wrong with the plumbing that I just don’t know where to turn.
Can you help me?
19 Nov 2001 at 1:15 am #291848SylvanLMPParticipant
Wow, another non returning contractor hits the dust trail
Now you can fully understand why I strongly feel the average home owner is far better off going to a home center buying the materials and doing the work themselves.
Storm drainage is not like a lot of USA handymen think with a hit and miss approach.
Storm drainage is much more complicated then regular house / office building plumbing drainage systems.
To “Properly” size storm water piping like for example roof or area drainage we measure square footage of drainage area and then contact the national weather service to get a 10 year frequency report for the exact area we are going to install the drainage piping so we can get an idea of “average” rain fall for a given area.
This is why all master plumbers should be held 1 million percent accountable if their measurements are wrong as they are supposed to know not guess sizes.
Not the engineer but the plumber is responsible hopefully and should be liable.
We calculate flow rates based on how many fixture units we are dealing with like combined flow and if the municipal storm lines are large enough.
This is why plumbers have to know when to install a controlled flow devices not to have a flooding or over loading the system.
For example we look at local codes and weather charts and by interpolation we find how many feet of drainage will become GPM flow (3 Square feet for example in some codes are considered 1 FU or 7.48 gallons after the 1st 10,000 ft etc. simple stuff huh?).
Do you have any sump pumps connected to this system as every GPM of a pump is also considered 1 FU
We also have to consider “pitch” of the roof/drainage area’s as the more incline the more gallons of flow we will encounter and thus larger piping must be used.
The conductors from the roof like leaders and or gutters also have to be properly sized and pitched with scupper boxes placed to protect the roof from possible heavy ponding which can cause a cave in (1 Cubic foot of water weighs over 62 pounds) and most non promenade decks are designed for weather protection (30 pound design weight per Sq. ft) and really offer no load bearing weight factors like normal decking. Normal is 125 per Sq. ft.
If you would be so kind as to E mail me with your exact area (I need this for 10 year frequency flow rates)
And the square footage of the areas to be drained.
If possible the roofing materials (KMM,EPDM,slate,BUR,SIS, Gravel, river bed rock for ballast, Koppers, etc) then by knowing the roofing membrane/insullation type I can figure out the flow restriction factor.
Some contractors do install reversed insulation as it is much easier to find roof penetrations without insulation under the bitumen membrane
Is this a pitched roof or flat and if pitched what degree?
This does not have to be exact as I use a fudge factor incse of leavs or other debris blocking the strainer, leader head etc.
Normally a flat roof has a design load of “only” 30 pounds per sq. foot, this of course is for allowing a build up of no more then 3″ of water
Ask your plumber at what flow rate did he/she figure for design of the size of the pipe?
The key in this profession is to actually know our job BUT in some cases this is not the normal. That is why we have lawyers as a counter measure for the simple mistakes some contractor make.
20 Nov 2001 at 9:44 am #291849bungieParticipant
And if he used 90mm then a bobcat to backfill, he could have squashed the pipe.
Where in Brisbane are you ??’
All advice is given with-out seeing the job, and hence all advice MUST be taken as advice with limited knowledge on the exact situation. NO responsibility can or will be taken. And yes, I am a licensed Plumber and Drainer with my own business in Brisbane Australia
- You must be logged in to reply to this topic.