A Sears softener has dry salt storage. The only time there should be water in the brine tank is during a regeneration. The first cycle of the regeneration is refill, then brine draw/slow rinse, then backwash, then fast rinse, then into service. The water level during service should be no higher than the suction port of the float valve ie:2″.
Regards, H2O Guy