Check your expansion tank if it is waterlogged then it would cause your pump to cycle on and off due to the small volume it would be operating in.
The only way an expansion tank can drain is for air behind the bladder to push it out. If your tank does not drain completely than it does not have enough air in it to displace the water inside.
Try pushing in the air valve on the tank to see if any air comes out. If no air comes out or very little it is full of water and is waterlogged if water comes out of the air valve then this would indicate the tank is bad.
If you have air in your water than your expansion tank needs to be replaced because the bladder has a hole in it.
To drain an expansion tank
First you need to drain the tank as far as it can go by itself. Next using a bicycle tire pump add air to the tank only until the water begins to flow out. Do not over pump the tank or you may ruin the bladder. Keep doing this until you are sure all of the water is out of the tank. Now to obtain the propper air pressure this can only be checked with the tank empty. Most well tanks use 38 PSI empty this pressure is usually 2 pounds less then the rated pressure switch. Now it would be a good time to disinfect the storage tank with some bleach. Use an empty filter sump housing to introduce about a 1/4 cup of bleach into the tank you will need some valves to do this. Now rinse the tank by filling it and draining it sevrall times.